Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Why can't I get a 4-20mA signal out of a Momentum 170AAO92100 analog output module when measuring across the output channels with a meter?
Causes and Fixes
Since the 170AAO92100 module has a load impedance specification of 600 ohms maximum for 4-20mA, usually a meter cannot be used to verify current output due to its high impedance. Therefore, it is recommended to wire a 250 ohm load resistor across the channel and measure voltage across it. The voltage should vary 1-5vdc corresponding to 4-20mA. Alternatively, if there is an existing analog input card with a spare 4-20mA channel, then the analog output can be wired to the analog input to verify the correct current output of the 170AAO92100.