Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The ETY4103 cannot find the configured IO Scanner devices after starting the PLC immediately following download
of a UNITY or PL7 application.
Facts and Changes
TSX ETY 4103 version 4.0
Causes and Fixes
Configured IO Scanner devices cannot be found after starting the PLC immediately following a
download of the Premium PLC application. If you try to ping the ETY module, the test fails. If there
are no devices connected to the ETY module and the IO scanner table is configured, the debug
screen in UNITY will not show the error condition correctly. Resetting the PLC using the 'Reset' button
on the PLC or power cycling the PLC corrects the problem.
This is an outstanding issue that is part of another problem which has been fixed in an improvement of
the IO scanner. The fix will be included in the next version of the exec firmware for the ETY4103.
The problem is due to the time that it takes to boot up the CPU being longer than the time it takes the ETY
module's IO scanner to bootup. This was a results of some organizational changes made in 'Executive
Firmware version 4.0'. The problem does not happen if you wait about 30 seconds after downloading
the PLC application.
As a workaround, you can either: