Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The purpose of this resolution is to remind CANopen network users of an important object that is required when STBNCOxxxx interfaced islands have analog modules installed in them.
Facts and Changes
According to CANopen standard DS-401, PDO transmission of analog input data is only possible if object 6423h is set to 1. Per the standard, default for this object is disabled (sections 6.2.7, 6.2.9 and 6.2.11).
Causes and Fixes
The following is an excerpt from STBNCO2212 documentation: