Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The purpose of this resolution is to remind CANopen network users of an important object that is required when STBNCOxxxx interfaced islands have analog modules installed in them.
Facts and Changes
According to CANopen standard DS-401, PDO transmission of analog input data is only possible if object 6423h is set to 1. Per the standard, default for this object is disabled (sections 6.2.7, 6.2.9 and 6.2.11).
Causes and Fixes
The following is an excerpt from STBNCO2212 documentation: