Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The purpose of this Resolution is to inform users of the 170FNT11001 of a potential problem with a specific range of manufactured modules that will not work when placed on the FIPIO fieldbus network.
Goals and Symptoms
The symptom is the PL7 software debug screen shows the nodes are not present or different from the configuration. The LED's in the fault condition are: RUN LED on, COMM LED blinks, and ERRor LED is off.
Facts and Changes
Approximately 700 units were manufactured with the wrong firmware installed. Affected units are 170FNT11001's with the serial number range of 210717xxxxx to 210724xxxxx.
Also reference Quality Bulletin IQ071495.
Causes and Fixes
Modules within the serial number range mentioned above must be exchanged. Firmware for this communication adapter cannot be upgraded in the field.