Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
How to improve the performance of searching for a register on a large project.
Facts and Changes
All versions of 'ProWORX 32'
Causes and Fixes
Searching for a register that is used in every network of a large project that contains 1000 or more
networks can take up to 30 minutes, when the project is connected to the PLC in either Online or
Combined mode. The problem is due to the constant updating of the opened Logic window and the
caching/display of the search results taking place at the same time.
To workaround this problem, close the Logic window before starting the search. After the search is
completed, re-open the Logic window. 'ProWORX 32' will remember the network that was last
displayed when the Logic window was closed.
A search for a register that is used in every network of a 1600 network project will take about 2 to 3
minutes using this workaround
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!