The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
How to improve the performance of searching for a register on a large project.
Facts and Changes
All versions of 'ProWORX 32'
Causes and Fixes
Searching for a register that is used in every network of a large project that contains 1000 or more
networks can take up to 30 minutes, when the project is connected to the PLC in either Online or
Combined mode. The problem is due to the constant updating of the opened Logic window and the
caching/display of the search results taking place at the same time.
To workaround this problem, close the Logic window before starting the search. After the search is
completed, re-open the Logic window. 'ProWORX 32' will remember the network that was last
displayed when the Logic window was closed.
A search for a register that is used in every network of a 1600 network project will take about 2 to 3
minutes using this workaround
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!