Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
How to write to the coils of a Quantum PLC using a WRITE_VAR
Facts and Changes
PL7 and UNITY
Causes and Fixes
The following example demonstrates how to use a WRITE_VAR to write to the coils of a Modicon
Qunatum PLC, using an '140NOE771xx' Ethernet module.
Writes coil 000023 through 000026 in a Quantum PLC that is configured for Modbus address 20.
Expression (3.120) instructs the WRITE_VAR to send the command out of XWAY address 3.120.
A value of 100 is added to the Modbus address for defining the XWAY address to a Modbus device.
The XWAY address must also be defined in the 'Connection Configuration' table of the Premium
Ethernet module device port configuration.
Expression 4.0.1 invokes the WRITE_VAR command to send the data out of
'Module 4', 'Channel 0', 'Sender address Ad0=1' in the Premium PLC. For a Modicon
device, the Sender address Ad0 is alsways equal to 1.
Expression '%M',22,4 will write four bits to coil 000023 through coil 0000026 in the Quantum PLC. The
reason for the offset is because Premium starts of with internal bit %M0 and the Quantum starts with
Expression %MW920:1 is used for the starting word of the 'Transfer Table' with a length of 1 word. The
bit structure is reversed for the transfer table. (i.e., word 920 is represented as 2#0000 0000 0000 1111
in the PL7 animation table for the four bits written in the above instruction.
Expression %MW925:4 is the starting word for the 'Management Word' table with a length of 4 words.