Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
This resolution describes a different behaviour of latched coils in Modsoft and Concept
Causes and Fixes
Under Modsoft, after uploading and then downloading the StateRAM, the values of the latched coils
appear as they were during the Upload.
Under Concept, after uploading and then downloading the StateRAM, all values of the latched coils
are resetted. The Concept Upload/Download function doesn't care about the usage of the 0x/1x values
because it has no information whether a 0x register is used as a latched coil.