Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Unity Pro V2.x
Virgin CPU 311 10 and CPUx34xxU sometimes doesn't start automatically after power cycle although they were in RUN mode before power off.
Causes and Fixes
Workaround: Connect to the PLC and perform a 'Backup clear'
The bugfix will be with the EXECs which are delivered with Unity version 3.1 and higher