Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The purpose of this resolution is to explain why a resistor is added across switching devices connected to a 140DSI35300 Supervised Input Module.
re: Modicon Quantum Automation Series Hardware reference Guide, p/n 840USE10000
Facts and Changes
If the field connection is good, when the switching device connected to a module input is open circuit, this shunt resistor completes the circuit and provides a small current sensed by the module. This current indicates that field wiring is not interrupted and a complete circuit exists.
Causes and Fixes
The resistor selection is sized so a minimum input current of 0.15 mA is maintained. If input current drops below that, the module will signal a broken field connection in the appropriate bits of I/O mapped Broken Wire registers #3 and #4.