Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The purpose of this resolution is to explain why a resistor is added across switching devices connected to a 140DSI35300 Supervised Input Module.
re: Modicon Quantum Automation Series Hardware reference Guide, p/n 840USE10000
Facts and Changes
If the field connection is good, when the switching device connected to a module input is open circuit, this shunt resistor completes the circuit and provides a small current sensed by the module. This current indicates that field wiring is not interrupted and a complete circuit exists.
Causes and Fixes
The resistor selection is sized so a minimum input current of 0.15 mA is maintained. If input current drops below that, the module will signal a broken field connection in the appropriate bits of I/O mapped Broken Wire registers #3 and #4.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!