Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The purpose of this resolution is to alert STBEHC3020 users to the effect of using Run Time Parameters to do a count preset.
Facts and Changes
When the Run Time Parameters feature is used to Preset the count value in an STBEHC3020 HSC marked SV: 01.60 or lower, the existing count value will go to zero and no further counting will occur. The counter validity bit will also be zeroed.
Causes and Fixes
If a Direct Counter Reset is issued after an RTP Preset, the new Preset value will take effect and counting will begin. If the Direct Counter Reset bit was set at the time of the RTP Preset, an island power cycle will be required to allow EHC operation to continue.