Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The purpose of this resolution is to inform users of Momentum 170LNT71000 Devicenet Communication Adapters of an issue with firmware version 1.21.
Facts and Changes
If operating for more than 30 seconds after the network becomes active, bidirectional discrete base outputs can freeze at last value when the LNT DeviceNet adapter loses fieldbus communication.
The issue will occur if a Devicenet Comm Adapter version 1.21 is mounted on a bi-directional module and both Polled and Strobed modes are selected at the same time in the Devicenet Scanner IO Parameters.
Causes and Fixes
At this time, a workaround to this problem involves selecting only POLLED mode in the Devicenet Scanner when using bi-directional modules.
Devicenet Communication Adapters that have firmware version 1.21 installed are:
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!