Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Connection issue between PL7 PRO with XIP driver to TSX MICRO connected on Ethernet with TSX ETZ 510
Goals and Symptoms
After a communication closure with TSX PREMIUM ,then opening a new one with a TSX MICRO , without the closure of PL7 PRO , it is impossible to connect to the TSX MICRO .
Causes and Fixes
Solution 1 : close PL7 , open again , define address of TSX MICRO , connection : OK
Solution 2 : Without closure of PL7 , create new PLC TSX MICRO , define address of PLC , connection : OK