The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
To inform users the byte order of MBP_MSTR "Get Local Statistics" Board Status for different 140NOE77101/11 and 140NOE77100/10 versions and which order will be consistently used for future product releases.
Facts and Changes
1. 140NOE77111/01 & 140NOE77100/10 MBP_MSTR Get local statistics Word3 board status:
140NOE77111/01 V2.0, V3.0, V3.1, V3.3, V3.6 & 140NOE77100/10 V3.0, V3.3, V3.4 has the same order as the table below:
|15||0=link LED off; 1= Link LED on|
|14||0=Application LED off; 1= Application LED on|
|13||0=twisted pair; 1=fiber|
|7... 4||Module Type|
|2||0=half duplex; 1=full duplex|
|1||0=not configured; 1=configured|
|0||0=PLC not running; 1=PLC/NOE running|
|10||0=half duplex; 1=full duplex|
|9||0=not configured; 1=configured|
|8||0=PLC not running; 1=PLC/NOE running|
|7||0=link LED off; 1= Link LED on|
|6||0=Application LED off; 1= Application LED on|
|5||0=twisted pair; 1=fiber|
Causes and Fixes
We have swapped MBP_MSTR Get local statistics Word3 board status byte order when we released certain firmware versions. This also causes the product user manual, and Unity, Concept Help file board status description mismatch issue.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!