Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Modbus exception code gets returned when downloading to a TSX Compact E2xx PLC via the ETG100.
Facts and Changes
Using the pinout for case 1 from page 7 of the 'ConneXium TSXETG100 Ethernet Gateway
Serial Connection Cases' document, results in a Modbus exception error code being returned when you try to
download a Conecpt application to a TSX Compact E2xx PLC.
Causes and Fixes
The pinout diagram is missing the connection for the jumper from the GND pin.
To resolve the problem, make the ground connection as show below.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!