Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Selecting INTEG, LLAG, LKUP or LIMT as the PCFL function type returns the wrong block type.
Facts and Changes
ProWORX32 Version 2.0C
Causes and Fixes
'ProWORX 32' appears be incorrectly selecting the wrong PCFL block function code for the top node.
of the block (The top node defines the library function type) when it is being configured in either 'Combined'
or 'Online' mode.
This only affects the selection for the LKUP, INTEG, LMIT and LLAG function types. Other function types
of the PCFL block are not affected.
This does not affect the operation of the PCFL block function. If you double click on the block after the
'Instruction Editor' window is closed, it will show the correct PCFL function type in the top node of the block.
(If you open the Intstruction Editor window to verify this, do not click on the OK button because it will change
the selected function type. Click on the Cancel button to exit out.) Also, the Data\Instruction Editor view will
show the correct registers for the function type.
As a workaround,