The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Selecting INTEG, LLAG, LKUP or LIMT as the PCFL function type returns the wrong block type.
Facts and Changes
ProWORX32 Version 2.0C
Causes and Fixes
'ProWORX 32' appears be incorrectly selecting the wrong PCFL block function code for the top node.
of the block (The top node defines the library function type) when it is being configured in either 'Combined'
or 'Online' mode.
This only affects the selection for the LKUP, INTEG, LMIT and LLAG function types. Other function types
of the PCFL block are not affected.
This does not affect the operation of the PCFL block function. If you double click on the block after the
'Instruction Editor' window is closed, it will show the correct PCFL function type in the top node of the block.
(If you open the Intstruction Editor window to verify this, do not click on the OK button because it will change
the selected function type. Click on the Cancel button to exit out.) Also, the Data\Instruction Editor view will
show the correct registers for the function type.
As a workaround,
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!