The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
To provide information about the problem of the 'Standby mode on logic mismatch' setting not working correctly.
Facts and Changes
ProWORX 32 version 2.0A
Causes and Fixes
The Configuration Extensions for the 'CHS' Hot Standby Loadable has a selection for the ''Standby mode (on
If you select the option as 'YES' in the setting for the 'Standby mode (on logic mismatch)', the Hot Standby PLC,
bit 13 of the command register gets set to a value of zero (0).
If you select the option as 'No' in the setting for the 'Standby mode (on logic mismatch)', the Hot Standby PLC,
bit 13 of the command register gets set to a value of (1).
This is acting in reverse to the expected behavior.
To resolve the problem:
(Removed File URL: 177427_B572/Hot_Standby_Mode_on_Mismatch.zip)(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/532c5360e3d9ef97c1257164004c251d/fl_block_5/0.5E0?OpenElement&FieldElemFormat=gif)
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!