Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
No, If a value is forced into the variable attached to the ET output of the block; it will be updated with the timers internal value when the block is solved.
A variable time is created located to 400001 and it is given an Initial Value of 23 seconds.
The variable is attached to a TON block and downloaded to the controller with Initial Values.
When the controller is started and the block is set to solve the ET output will be updated with the internal time of the block.
Note: This applies to all / most function blocks either in Concept IEC or Unity Pro IEC.