Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
ProWORX 32 Appears to be solving some skipped networks when the SKP block is inserted in between logic
within the middle of a populated network
Facts and Changes
ProWORX 32 version 2.0
Causes and Fixes
If a SKP block is inserted in between logic within a populated network, it is possible to see power flow still occurring
in the logic on one of the networks that are supposed to be skipped.
Further examination of the registers associated with the logic within the network will in fact show that the
network has been skipped. In addition, the comment field located in the lower right corner of the Logic window
will display the comment 'Netwrok skipped'.
The problem is related to the display update.for the Logic window when the SKP block is used with logic in the same
As a workaround, the SKP block should be inserted in a network that does not contain other logic.