Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Why does the Input count range for the ADU205 Compact I/O module change after converting from
a Compact 984-A145 PLC to a Compact 984-E275 PLC.
Facts and Changes
The input count range for the ADU205 Compact IO module is defined as 2049-6143 for an input range of
-20mA to +20mA. When the PLC type is changed to 984-E275, the input count range is changed and the
module input irange s no longer valid for the application.
Causes and Fixes
According to the 'Modicon A120 Seris I/O Modules User Guide', this is a normal behavior for the module.
The problem is due to the different input resolution used for the 984-E2xx Compact PLC.
To resolve the problem:
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!