The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
This resolution has information for STB users that applies when an STBNIP2212 NIM interfaced island is operating in TEST mode.
Causes and Fixes
When IO scanner functionality is being used in the PLC to enable reading of island module inputs and diagnostic data, it is recommended to have the input and output areas on separate lines within the IO scanner. Otherwise, if the island is in TEST mode, the scanner will indicate an error and inputs will not be read. This is due to the nature of I/O Scanner operation when writes are prohibited by the island. It also applies to reading the HMI to PLC area.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!