Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
This purpose of this resolution is to provide information regarding hot swapping STB modules.
Causes and Fixes
The design of STB product does not allow the hot-swapping of an I/O module if there is only one module in the system. The same is true if you have multiple modules and you remove all of them prior to replacing one. The NIM will enter a fatal error condition if no I/O modules are present.