Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The purpose of this resolution is to provide the correct field wiring pinouts for the STBACO1225 Analog Current Output module.
Causes and Fixes
The STB Hardware Components Reference Guide, p/n 890USE17200, v3.0 and current STBSPU1000 (v2.00, 1/2006) on-line help incorrectly show pin 3 of the STBACO1225 terminal blocks as output to field actuators. Pin 2 is the correct output point for this module. The wiring diagram printed on the module's side is correct. Reference these illustrations for proper module wiring;
The following field wiring example shows how two single-ended analog actuators can be wired to the STBACO1225 module. Two separate external power supplies are needed to make sure that the proper current is delivered to each actuator.
If you want to use 24 VDC from the islands actuator bus to power a single-ended analog field device, this power can be delivered through the output module. To do this, use pins 1 and 6 as follows
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!