Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Unity Pro documentation states that you cannot manipulate any variables in the monitoring mode, however users have found that it is possible.
Facts and Changes
Unity Pro V2.2 and older.
Causes and Fixes
This is a known issue and will be fixed in a future Unity Pro version. For example, users accessing the PLC can modify variables in the animation table. The future release will prevent any modification to the PLC in the monitor mode.