Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Due to the evolution in the memory market the ASFLSH004 had to be changed to manufacturer Pretec. The internal timing of the new Flash card is slightly different to the old one. This could cause timeouts during programming with e.g. Proworx or Concept together with Compact EXECs older V2.18E. If the flash is programmed no functional problem in the CPU with older EXECs is known.
Facts and Changes
ASFLSH004 from manufacturer Pretec
Compact EXECs older V2.18E
Causes and Fixes
Use the EXEC V2.18E or newer for all Softwareversions of Modsoft, Proworx and Concept V2.5 or newer. Concept V2.2 and older cannot use this EXEC and should be updated to the newest version of Concept (actually Concept V2.6 SR3).