Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes you can use FDR with only the rotary switches configured.
The role name to use in your FDR Server (Quantum/Premium) is STBNIP2212_<numeric setting of rotary switches>. For example, if you set the switches to the value 110, enter the FDR role name in your FDR server as STBNIP2212_110. The Advantys will then assume the configured IP Address parameters and backup configuration. Note that the values are significant. When setting a device to rotary switch settings 10, use STPNIP2212_010 to use all 3 possible digits.