Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Viewing the 'Diagnostic' web page of a Quantum 'NOE 771 xxx' module could return the error message
'IEC program not available'.
Facts and Changes
Attempts to view the diagnostic web page of a Quantum '140 NOE 771 xx' module whose PLC configuration was
configured using ProWORX 32, could return the error message 'IEC program not available' if the NOE is configured with
a executive firmware version 3.3 or lower.
Causes and Fixes
This is due to the Quantum PLC having been previously configured with a Concept 'IEC' application or a Concept
984 application that had the IEC option checked off in the plc configuration..
To resolve this problem, download a Concept configuration (make sure that the 'IEC' option is deselected) to the
PLC and then re-download the ProWORX 32 project.