The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Viewing the 'Diagnostic' web page of a Quantum 'NOE 771 xxx' module could return the error message
'IEC program not available'.
Facts and Changes
Attempts to view the diagnostic web page of a Quantum '140 NOE 771 xx' module whose PLC configuration was
configured using ProWORX 32, could return the error message 'IEC program not available' if the NOE is configured with
a executive firmware version 3.3 or lower.
Causes and Fixes
This is due to the Quantum PLC having been previously configured with a Concept 'IEC' application or a Concept
984 application that had the IEC option checked off in the plc configuration..
To resolve this problem, download a Concept configuration (make sure that the 'IEC' option is deselected) to the
PLC and then re-download the ProWORX 32 project.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!