Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Viewing the 'Diagnostic' web page of a Quantum 'NOE 771 xxx' module could return the error message
'IEC program not available'.
Facts and Changes
Attempts to view the diagnostic web page of a Quantum '140 NOE 771 xx' module whose PLC configuration was
configured using ProWORX 32, could return the error message 'IEC program not available' if the NOE is configured with
a executive firmware version 3.3 or lower.
Causes and Fixes
This is due to the Quantum PLC having been previously configured with a Concept 'IEC' application or a Concept
984 application that had the IEC option checked off in the plc configuration..
To resolve this problem, download a Concept configuration (make sure that the 'IEC' option is deselected) to the
PLC and then re-download the ProWORX 32 project.