The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
If an I/O module is removed in the middle of an island, all the remaining modules function properly.
However, when the island is power cycled then only the modules to the left of the missing module run properly. All the modules to the right do not run. If the missing module is re-inserted, all the modules begin functioning properly again. This occurs due to the fact that if a module is removed, on a power cycle the auto configuration and addressing cannot be completed (auto addressing line open on bus) causing the module to be not detected.
This explanation is described in the Advantys STB System Planning and Installation Guide (890USE17100), in the section titled "Commissioning an Advantys STB Island".
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!