Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
If an I/O module is removed in the middle of an island, all the remaining modules function properly.
However, when the island is power cycled then only the modules to the left of the missing module run properly. All the modules to the right do not run. If the missing module is re-inserted, all the modules begin functioning properly again. This occurs due to the fact that if a module is removed, on a power cycle the auto configuration and addressing cannot be completed (auto addressing line open on bus) causing the module to be not detected.
This explanation is described in the Advantys STB System Planning and Installation Guide (890USE17100), in the section titled "Commissioning an Advantys STB Island".