Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
IEC & 984LL hybrid projects with many variables can take a very long time to analyze due to checking for multiple coils in the IEC and 984LL sections.
After installing Patch A for Concept 2.6 SR2, there are two possibilities to speed up the analyzing in mixed projects:
- by deselecting the analyzer option Show Warnings (all analyzer warnings are eliminated).
- by setting the option SkipMultiAssignCheckIecLL984=1 in the [Debug] section of the concept.ini file.
Only the check for multiple coils in IEC/984LL sections is skipped.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!