Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
IEC & 984LL hybrid projects with many variables can take a very long time to analyze due to checking for multiple coils in the IEC and 984LL sections.
After installing Patch A for Concept 2.6 SR2, there are two possibilities to speed up the analyzing in mixed projects:
- by deselecting the analyzer option Show Warnings (all analyzer warnings are eliminated).
- by setting the option SkipMultiAssignCheckIecLL984=1 in the [Debug] section of the concept.ini file.
Only the check for multiple coils in IEC/984LL sections is skipped.