Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Procedure to upgrade the 140NOE 771x0 Ethernet module from version 2.xx to version 3.30 or a later version.
Causes and Fixes
The NOE 2.xx cannot be directly upgraded to version 3.30 without first upgrading it to version 3.0. The NOE must first be upgraded to version 3.00 using the
instructions outlined in resolution 170858 before it is upgraded to version 3.30 or a later version.
Any attempt to update a 140NOE77x0 module directly to version 3.30 or a later version from version 2.xx will cause the module to become inoperable.
If this happens, the mudule will need to be sent back to Schneider Electric for repair.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!