Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Conclusion from several Magelis iPC failure analysis demonstrated that improper selection or use of UPS could easily damage iPC and create failures.
The goal of this resolution is to provide direction for UPS selection (use of UPS must follow UPS user manual instructions).
Facts and Changes
For reference, we shortly explain here under the 3 different uninterruptible power supply (UPS) technologies:
Causes and Fixes
As a principle, the only technology that fits for Industrial PC is the double conversion.
According to functional and environmental tests, we strongly recommend to use UPS units from the MGE Pulsar EXtreme C range UPS to protect Magelis iPC.
The MGE Ellipse and Pulsar Evolution ranges are not satisfactory to work with Magelis iPC and may cause failure.