Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
ProWORX 32 returns a Runtime Error 2015 when it is installed and started on a PC that has 'Delta V' software.
('Delta V' is a third party software from Emerson.)
Facts and Changes
The 'ProWORX 32' and 'Delta V' both use a third party software component called 'Ina'. Unfortunately, the Delta V
software is using an older version of the shared 'Ina' Active-X controls. This older version is causing the Runtime
Error 2015 to occur when ProWORX 32 is started.
Causes and Fixes
The following procedure can be used to resolve the problem:
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!