Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
This recommendation applies to TSXPSY2600M, TSXPSY5500M and TSXPSY8500M , AC power supplies of the Premium range.
Goals and Symptoms
TSXPSY2600M, TSXPSY5500M and TSXPSY8500M provide a 24 VDC auxiliary voltage for powering of I/O APS_SENSORS and actuators. The characteristics of the total consumed current must be in accordance with the possibilities (inrush current, nominal/normal current ..etc .) of this power supply.
The "load" must be as resistive as possible to be sure to obtain good results.
This precaution must be followed as close as possible to avoid problems like stop of CPU (indirect effect on the internal 5V).
For example, the use of this auxiliary voltage to "feed" an Advantys station (by its own power supply) is strictly inadvisable.
Facts and Changes
This resolution is only to prevent dysfunctionning by a bad use of this auxiliary voltage.
Causes and Fixes
See OPR #20026433. No vantive case (problem seen internally)