Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
From the Modbus Plus Target screen, you can scan your network and select the Modbus Plus Target Address by highlighting the Node and then select the Properties button. Note that you can also use the USB or Modbus link.
You will be prompted to "Stop" the PLC during this operation.
You can also perform the same task with a Premium using USB or Unitelway.
Connecting via TCP/IP (FTP) is not an option as the Query will result in the Ethernet Coprocessor firmware version and not that of the CPU.
Another window will open showing Device Properties.