The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Documentation of TCP/IP statistics insufficient MBP_MSTR function 3
Facts and Changes
Unity-Pro v2.01 Primary 140NOE77111 v3.5 Connected at 10MB/HDX
Get local statistics word 3
1100 0011 1000 0000 c380: OK
1100 0011 0001 0000 c310: Disconnected NOK flash
1100 0111 0011 0000 c730: Disconnected NOK flash 2
Description in helpfile/manual, online describe bit 0, 14 and 15. What is the meaning of al these bits in the status register?
Causes and Fixes
The description on the help/online file in Unity pro is not correct for the NOE version 3.5. The description refers to the older version of NOE, corrections will be made for the documents.
Please refer to the information on page 147, Modicon Quantum with Unity Ethernet Network Modules User Manual, UNY USE 100 10 V20E, September 2004
The correct bits that you need to monitor are bits 6, 7, 8 respectively if you would like to see the APPL, LINK or RUN led status.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!