The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
ProWORX 32/ NxT Data Watch Window is unresponsive to inputs after the log is stopped.
Facts and Changes
If you try to make any changes (i.e., disable a 1x or 0x reference, etc.) in the Data Watch Window after stopping the log, the Data Watch Window does not respond to the user action.
Causes and Fixes
This is the way the Data Logger works. When the Data Logger is running, anything shown in the Data Watch Window will reflect what is being logged to the log file. When the log stops recording, the data watch window will reflects the data in the first row of the log file. Any attempts to make changes to the references listed in the Data Watch Window does not work and the window appears to be unresponsive. The reason for this is because the user is not allowed to make changes the log file.
In order to male changes to the Data Watch Window (i.e., disable/enable the 1x or 0x reference, etc.) the Data Watch window must be switched from the 'Data Logging' mode to the 'Data Watch' mode. This is accomplished in ProWORX 32 by right clicking on the Data Watch Window and selecting 'Close Log File'.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!