Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The goal of this resolution is to clarify NIM holdup time operation for Advantys STB users.
Causes and Fixes
When the network head that writes to a NIM is stopped, an output module located in the NIMs island will maintain its output states from that time until any preprogrammed timeout value expires. After that, the predefined fallback states are then set.
However, if the network communication cable is disconnected at the NIM, island output module states are not maintained for the holdup time duration. They immediately go to the predefined fallback states.