Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Converting a ProWORX NxT application that has a Profibus configuration extension defined.
Facts and Changes
Convertion Modsoft - Concept
Causes and Fixes
Use the following procedure to convert a ProWORX NxT application that has "Profibus configured to a Concept project.
1.) Download the NxT project to the plc.
2.) Upload the plc application using Concept.
3.) Save the project.
4.) Check the configuration extension to ensure that the Profibus option is checked off.
5.) Check the IO Map to see if the 140 CRP 811 module is in the configuration.
6.) Click on the Params button in the IO Map to bring up the Profibus information for the CRP 811 module.
7.) Click on the button Add Upload Info.
8.) Click on the OK button
9.) Repeat steps 6 through 8 for each configured 140 CRP 811 module.
9.) Save the changes.
10.) Upload the plc application again.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!