Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Converting a ProWORX NxT application that has a Profibus configuration extension defined to a Concept application.
Facts and Changes
Convertion Modsoft - Concept
Causes and Fixes
Use the following procedure to convert a ProWORX NxT application that has "Profibus configured to a Concept project.
1.) Use ProWORX NxT to download the project to the plc.
2.) Use Concept to upload the project from the plc.
3.) Define the number of "Profibus configuration extensions
4.) Add the 140 CRP 811 module to the IO Map.
5.) Click on the 'Parameter' button to bring up the module parameters.
6.) Click on the 'Import' button to import the .cnf file for the Profibus configuration.
3.) Save the application.
The Profibus related configuration information for the 140 CRP 811 mdoule does not get uploaded from the plc.