Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The Unity-Pro project is transfered through the USB port and the connection is lost just after the Run command.
The animation remains frozen and the following message is displayed :
"PLC failed - Automatic return to off line"
The PLC remains in Run mode, every time you try to connect it again the same message is displayed.
Causes and Fixes
The connection is lost because the project has a long Scan Time and the request takes more time than the driver timeout to get an answer.
You have to change the timeout of the driver, for that :
- Under Unity-Pro, select in the menu PLC -> Set Address,
- In the PLC area, click on the "Communication Parameters" button,
You can increase the Timeout to 10 seconds in order to stay connected.
-Click OK to validate.