Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
An issue has been found with the combination of a 174CEV30020 V1.3 Modbus/Ethernet gateway and a 984B controller connected over RS-232 at 19,200 baud .
Facts and Changes
The 984B worked fine with the 174CEV30010 at 19,200 baud and it works fine at 9,600 baud with the 174CEV30020
Causes and Fixes
Since this problem only seems to happen with this combination and this is a new exec that solved similar issues in many other environments there is no planned change to address this issue. Therefore we do not recommend using 174CEV20030 and 984B controllers at 19,200 baud.