The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Maximum drop length is 164 feet.
Minimum drop length is 8.5 feet.
Maximum trunk length is 8400 feet using RG11 and 4600 feet using RG6.
Maximum overall attenuation for the network is 35 db.
Minimum distance between taps is 8.5 feet.
Minimum distance between the RIO head and the self terminating "F" adapter is 18 inches.
Minimum distance between the self terminating "F" adapter and splitter 8.5 feet.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!