Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Maximum drop length is 164 feet.
Minimum drop length is 8.5 feet.
Maximum trunk length is 8400 feet using RG11 and 4600 feet using RG6.
Maximum overall attenuation for the network is 35 db.
Minimum distance between taps is 8.5 feet.
Minimum distance between the RIO head and the self terminating "F" adapter is 18 inches.
Minimum distance between the self terminating "F" adapter and splitter 8.5 feet.