Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The purpose of this document is to describe what options are available to log activity on the 174CEV20030
Facts and Changes
To use the logging features of the !74CEV20030 you need to have a keyboard and monitor connected to the Briidge.
Note: Turning logging will affect the performance of the bridge so be careful in using it. It is good to use for troubleshooting but should not be left on for normal operations.
Causes and Fixes
The bridges enables and disables logging by entering specific keys on the keyboard. An uppercase character will turn logging on and the same lowercase character will turn it off.
A. Ethernet generated ModbusTCP packeta and direction of travel and session number
B. Modbus Plus Generated Modbus packets and direction of travel and path number
G. Routine messages showing internal Bridge activity for Modbus Plus generated messages
H. Path information used in Bridge
N. System timing tick
O. Routine messages showing internal Bridge activity for Ethernet generated messages
P. Internal bridge errors