Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
How can I determine if an AC powered inductive device can be used with a Quantum relay module?
Causes and Fixes
Published VA ratings can be used to determine if a product may be used.
Maximum contact current is 2A for the 140DRA84000 and 5A for the 140DRC83000.
The maximum 120VAC load VA rating for the DRA module is 120 x 2 = 240VA.
The maximum 220VAC load VA rating for the DRA module is 220 x 2 = 440VA.
The maximum 120VAC load VA rating for the DRC module is 120 x 5 = 600VA.
The maximum 220VAC load VA rating for the DRC module is 220 x 5 = 1100VA.