Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
When an over-utilized flag is received in the Resource Analysis, a build of your project will not be allowed. Therefore two options are available. One option is to create another island (requiring another NIM). The second option is to create an extension segment. Creating an extension segment requires an EOS (end of segment) module at the end of the primary or previous segment and a BOS (beginning of segment) module at the beginning of the extension segment. The BOS module would supply an additional 1.2 A for its segment. Up to six extension segments per island are allowed. Any module beyond the available logic power would not initialize.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!