The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
When an over-utilized flag is received in the Resource Analysis, a build of your project will not be allowed. Therefore two options are available. One option is to create another island (requiring another NIM). The second option is to create an extension segment. Creating an extension segment requires an EOS (end of segment) module at the end of the primary or previous segment and a BOS (beginning of segment) module at the beginning of the extension segment. The BOS module would supply an additional 1.2 A for its segment. Up to six extension segments per island are allowed. Any module beyond the available logic power would not initialize.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!