Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
No. The AS-E908-031 executive cartridge are not compatible with the PC-E984-X8X at any prom combo. If a user is migrating from a PC-0984-X8X controller to a PC-E984-X8X controller and if the executive cartridge in the S908 Remote I/O module is a AS-E908-031, then the user must purchase a new executive cartridge. The current part number is AS-E908-131. Its current prom combo is 1011. The minimum prom combo required for the AS-E908-131 executive cartridge to be compatible with the PC-E984-X8X controller is 1007.