The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
FAULT ILF IN ALTIVAR 58. WHEN REPETITIVE UDP FRAME OF 1525 BYTES (POLLING RATE 5 MS) IN NET.
Facts and Changes
16 UNITS OF VW3A58310. WHEN REPETITIVE UDP FRAME OF 1525 BYTES POLLING RATE 5 MS
Causes and Fixes
Be careful, with UDP there is no guarantee on the datagram validity , if the datagram in not complete the inverter will trip in ILF, and it's necessary to have some time to analyse 1525 bytes and a clogging is possible at the input card, try to increase the polling and if it's possible use the TCP mode.
USER MANUEL P100 English version : The Ethernet card is compliant with ETHERNET 2 frames format (IEEE 802.3 is not supported).
If you server can support only this mode, the only solution is to replace it.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!