Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
FAULT ILF IN ALTIVAR 58. WHEN REPETITIVE UDP FRAME OF 1525 BYTES (POLLING RATE 5 MS) IN NET.
Facts and Changes
16 UNITS OF VW3A58310. WHEN REPETITIVE UDP FRAME OF 1525 BYTES POLLING RATE 5 MS
Causes and Fixes
Be careful, with UDP there is no guarantee on the datagram validity , if the datagram in not complete the inverter will trip in ILF, and it's necessary to have some time to analyse 1525 bytes and a clogging is possible at the input card, try to increase the polling and if it's possible use the TCP mode.
USER MANUEL P100 English version : The Ethernet card is compliant with ETHERNET 2 frames format (IEEE 802.3 is not supported).
If you server can support only this mode, the only solution is to replace it.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!