Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
We have some problems with ATV31 and LA9P307. Normally it works well but not in this case: LA9P307 with HUB LU9GC3 and 8 ATV31. RC-Termination is like manual. It works well but when one ATV31 is shut off or disconnect from Modbus the other 7 atv31 are tripping with SLF!
When it will be switched off it gives for a short time 208 in the ETA
Facts and Changes
ATV31 Modbus LA9P307
Causes and Fixes
What is the adjusting value of PPO failure ? The problem was solved with Modbus max N adjusted to 2 in place of 7. The signification of 16#0208 in ETA is serial link fault. It was siemens PLC.