Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
We understand there is a EMC filter switch in ATV31 range( up to 7.5Hp), and it can be lifted if its power is a I.T. system.
1. Actually, we was told there is a very few power system using I.T. system. Could you please give us examples what condition and what EQUIPMENT must use I.T. system? Is there any country use this I.T. system?
2. What would be problem if this EMC filter switch not disconnected in I.T.system?
Causes and Fixes
The current of first insulating defect is limited, by the impedance connection with the ground of the point medium of the transformer (2000 ohms), and with a value such that does not result from dangerous voltage of contact. i=230V/2000 ohms = 100mA (simplified equation) protection does not require a cut, which makes it possible to maintain the continuity of service. With the second insulation defect , the automatic cut must intervene. The defect phase/ground degenerates into short-circuit equivalent to a defect phase/phase. The device safety against the courts - circuits (circuit breaker) thus it will locate and cancel it instantaneously. Protection against the indirect contacts is ensured by the circuit breakers with rate IT. The differentials are useless (N.B.: the pole of neutral must also be protected).
This neutral mode is used for continuity service, use in a lot of countries ( France for example ).
EMC filter capacitors could be damaged because of an overvoltage in case of contact between one input phase suplly and the earth.
The leakage currents generated cause a dysfunction of the insulation fault detection devices (Permanent Insulation Monitor (PIM) or Residual Current Device (RCD)
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!