The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Hi, We did promotion on the ATV58 with the ethernet optionmodule (V2). We are using the rollname (DHCP) service and FDR . This is working fine , but on one condition these features are not working. When the ATV is powered off , and the switch or hub to whom he is connected aswell. Power on the Altivar first and after a minute the switch or hub, then the altivar will not obtain his IP adres. We have a similar situation with the STB modules . This is urgent.
Facts and Changes
Causes and Fixes
Running of DHCP and FDR :
After power on, the option card send the DHCP requests during a time of 64 sec, so if you power on the switch or hub after 1 min ( 60 sec ) there is not enough time to receive the DHCP answer and the card is lock, you can verify this with the embedded server and the FDR status.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!