The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Refreshing time of Variables for Communication propose What is the frequence of updating of Variables available for communication in ATV68 EX: W1030 if configured to be a Speed in RPM?
Facts and Changes
Causes and Fixes
The ATV68 decides between the PZD communication channel and the PKW.
At the Profibus link both parts have to be transmitted from PLC to the drive. (PPO1- PPO4). Each PZD telegram will be worked out within a 5 ms task. A PKW telegram (read/write a parameter) will be worked out in a 100ms
task. Using the Profibus connection, it will be necessary to send the PKW request as long until you get a response.
By using the Gateways (separated PKW and PZD telegrams)for serial connection the time for the RS232 communication from drive to gateway has to be added.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!